Question about Square D Qo 100 Amp Breaker Box Qo120m100 Indoor Panel
Very simple: Unhook the wire from the breaker and then pry up at the center of the box... the breaker slips over a blade at the center of the box and tucks under a pair of tabs near where the wire connects.
That is, the breakers tip up from near the center of the box toward the outside.
You can use aa flat screwdriver to go right between the breakers at the center to nudge them up to start... DO NOT put the driver in more than 1/4 inch.
Posted on Sep 14, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 26, 2013 | Square D Co. HOM130C Circuit Breaker
Oct 27, 2012 | Electrical Supplies
Aug 24, 2012 | Square D Qo 200 Amp 40 Circuit Indoor...
Aug 15, 2012 | Square D Qo 200 Amp 40 Circuit Indoor...
Jun 24, 2017 | Computers & Internet
Feb 16, 2011 | Electric General Ted134050 50a 480v...
Aug 14, 2010 | Gb Electrical 100 Amp GE Load Center
Sep 04, 2009 | Coleman Heating & Cooling
Jun 04, 2009 | Dometic Rooftop RV Air Conditioner
130 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: