Question about Goodman GMS90703BXA Heater
The contactors will not stay in. unit will run only if i hold contactors in.
Loss of 24 volt power either from thermostat or transformer. Check for voltage across low voltage side of contactor (the small wires).
Posted on May 16, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 21, 2014 | Goodman 3 Ton 14 ee Goodan Heat Pump...
Jan 25, 2014 | Goodman Manufacturing Goodman GPH1348H41...
May 11, 2013 | Ruud 3 Ton Split System Heat Pump
Aug 17, 2012 | Goodman Heating & Cooling
Sep 26, 2011 | Goodman Heating & Cooling
Jul 09, 2010 | Goodman CLJ30AR32 Air Conditioner
Sep 19, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 21, 2009 | Goodman Heating & Cooling
Jun 06, 2009 | Goodman CLQ36AR49 Air Conditioner
73 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: