Question about LG LS240CE Split System Air Conditioner
CH-46.Outdoor unit suction sensor fault. Disconnect from PCB and measure resistance. 10 kOhm at 10°C and 4 kOhm at 30°C. If OK replace PCB, if not replace sensor.
Posted on Jan 01, 2011
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 01, 2015 | LG Heating & Cooling
May 12, 2014 | Heating & Cooling
Aug 01, 2011 | Mitsubishi Mr. Slim MXZ30TN Air...
Jul 05, 2011 | Heating & Cooling
Aug 11, 2010 | LG Art Cool LA181CNW Split System Air...
Nov 14, 2009 | Heating & Cooling
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
Jul 13, 2008 | Washing Machines
1,096 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: