Question about Reliance Water Heater #9003531 NAT Gas Pilot Assembly
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
this is either the thermocouple lead or the uni control i would replace the thermocouple leed first, these parts can't be repaired they have to be replaced
Posted on Jul 14, 2010
SOURCE: pilot hard to lite when
The thermocouple has gone bad or in this case is going bad to the point that it is useless.
The thermocouple is the pilot's, well, co-pilot! It is the electronic device that senses if the pilot flame is hot enough to ignite natural gas or propane fuel to the burner. If the thermocouple thinks it's safe, then it keeps open the main gas valve located in the pilot assembly. If the thermocouple does not sense enough heat from the pilot flame (such as when the pilot is out), then the thermocouple shuts off the gas valve to the burners.
How the Thermocouple Works
So what is this thing and how does it work? Well the thermocouple (technically called a thermocouple junction) is a device that contains two metal wires welded at the ends and placed inside a protective metal case. The thermocouple sensor is found at the business end of the pilot flame and is designed to be placed in the hottest part of the flame. The other end is connected to the pilot valve body. As the thermocouple heats up, it produces a small amount of electricity and when it gets hot enough from the pilot, send a signal to open the gas valve by using a solenoid operated by a 24 volt transformer. The thermocouple calls the shots, and by converting heat to an electrical signal, it allows the gas valve to open or close. Once the gas valve is open, gas is then constantly supplied to the pilot and as required for the gas burners (as called for by the thermostat). If the pilot goes out, then the thermocouple gets cold and produces no electric signal to open the gas valve's solenoid and the gas valve shuts off the gas supply to the pilot and burners. Neat huh?
Posted on Feb 04, 2011
If I understand correctly, the pilot light is not staying lit.
You light the pilot and water in the tank reaches temperature.
Once hot water is gone, then pilot light has to be lit again.
Gas pressure is good, and gas is flowing.
Thermostat is working at high end because it cuts off heating.
Vent is working because tank heats up.
Air intake is working.
Gas control thermostat might not be reading low temperature. Replace gas control valve.
Pilot tube might be dirty. Clean burner parts and combustion chamber, and air intake, and vent.
Backdraft might be blowing out pilot. Check for constant updraft by running water heater 5 minutes, and then light match under vent hood and see if smoke goes up.
Very hot air can put out pilot, especially when water heater located in attic. Add ventilation.
Improper vent might have water dripping back down into combustion chamber and putting out pilot light and rusting out the parts. Inspect for rusted parts and water.
Posted on Aug 10, 2011
Tips for a great answer:
Sep 13, 2013 | Bosch GWH 425 EF L Water Heater
Sep 08, 2013 | AO Smith PHPT-60 60 Gallon Voltex...
Aug 05, 2013 | Bosch PowerStar AE125 AE125 Whole House...
Jan 10, 2013 | Bradford White everhot outdoor tankless...
Jul 24, 2011 | RTO Atwood DSI-RV Water Heater-6 Gallon
Jun 24, 2011 | Audiovox Richmond 6G40-36F 6-Year Tall Gas...
Jun 22, 2011 | Water Heaters
Oct 03, 2009 | Rheem 81VP6S/430126 Water Heater
Nov 12, 2008 | Water Heaters
56 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: