Question about Bryant Heating & Cooling
First check the disconnect/circuit breaker that should be located close to the outside unit. Next remove the cover where the power goes into the outside unit so that you can see the contactor. Do a visual check of the contactor and contacts. Set the thermostat to make the A/C come, then look at the contactor to see if the contacts have closed. Use a voltmeter to check for power on the load side of the contactor. If the contacts didn't close, remove the thermostat face and install a jumper between R and Y terminals and see if it pulls in then. If it does then, the problem is your thermostat. If the contacts close and you have power check the capacitor next. If it looks swollen, it is bad - replace it, otherwise you can check it with a multimeter with the capacitor check function. Try these simple checks and let me know what you find if this doesn't fix it so I can give you some more things to look at.
Posted on Sep 13, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 28, 2017 | Bryant Heating & Cooling
Sep 03, 2011 | LG Electronic Window Air Conditioner
Sep 02, 2011 | Mitsubishi Heating & Cooling
Aug 27, 2011 | Coleman Heating & Cooling
Aug 23, 2011 | Goodman CKL62AR61 Air Conditioner
Aug 30, 2010 | Heating & Cooling
Jul 01, 2009 | Goodman Heating & Cooling
Jan 27, 2009 | Heating & Cooling
97 people viewed this question
Usually answered in minutes!