Question about McCall Refrigeration Commercial Freezer 11045UF01 Stainless Steel
If the condenser coil is clean and the unit is in an area where the ambient temp. is 80 degrees or less, it is most likely a refrigerant problem. Probably low and has a leak. Another issue could be that the line sizes for the distance the refrigerant has to travel, may be wrong. Since I don't know the distance, you may need to have that checked into also. You should not have more than a 1-2 psi drop due to line size and distance traveled.
Posted on Sep 13, 2010
Testimonial: "Many thanks for the concise reply! It's not good news, but now I'm comfortable calling a tech to check the original installation for leaks and sizes."
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 01, 2011 | McCall Freezer 7-7045FT
Jan 04, 2011 | Arctic Air 22 cu. ft. Commercial Freezer...
May 23, 2010 | McCall Freezer 7-7045FT
Jan 01, 2010 | Freezers
Oct 13, 2009 | Frigidaire Freezer 20.3 Cu. Ft. Frost Free...
Aug 27, 2009 | Kenmore Freezers
Jan 16, 2009 | Hoshizaki Freezer Commercial Ice Machines...
Sep 14, 2017 | Freezers
135 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: