Question about Sta Rite Ds3hf 1.50 Hp Self Priming Irrigation Pump
Likely two very separate problems:
Prime failure is either mechanical wear in the pump or an air leak in the suction line. It is usually easier to look for air leaks in the suction prior to disassembling the pump to look for trouble. A clogged foot valve, a clogged impeller, clogged inlet screens, etc.
Line leads discoloring can mean many things: Line voltage may be dropping too much and/or the line leads undersized. The motor may be beginning to fail causing an increase in amp draw. The pump may be overloaded but that is unlikely.
As you narrow down the possibilities please add comments to this post if you need additional guidance.
Posted on Sep 12, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 17, 2015 | Water Heaters
Apr 01, 2015 | Washing Machines
May 02, 2012 | Sta Rite Max E Pro 2 Hp Up Rate Energy...
Feb 19, 2011 | Bosch PowerStar AE9.5 AE9.5 Point-of-Use...
Dec 28, 2010 | RELIANCE ELECTRIC WATER HEATER
Sep 09, 2009 | Washing Machines
Aug 22, 2009 | Belkin (F6C800-UNV-PL) UPS System
Feb 02, 2009 | Kenmore 23822 Top Load Washer
Jan 28, 2009 | Kenmore 24032\24036 Top Load Washer
Oct 16, 2017 | Sta Rite Ds3hf 1.50 Hp Self Priming...
Jul 30, 2011 | Sta Rite Ds3hf 1.50 Hp Self Priming...
190 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: