Question about Whirlpool Heating & Cooling
You will need to check and make sure you are getting power to the outside unit at the contactor. If you are then you will need to see if it pulling the contact in, 26 volts, if it is not pulling in contact and has the voltage it is the contactor, if the contact is pulled in then make sure you have voltage going to the fan motor, if you do then it is the fan motor/capicator. Hope this helped Tim
Posted on Sep 11, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 11, 2014 | Bryant Heating & Cooling
Oct 08, 2013 | Gibson Heating & Cooling
Jan 18, 2011 | Samsung Heating & Cooling
Apr 14, 2010 | 2008 BMW 528i Sedan
Nov 06, 2009 | SkyScan 86742 Digital Atomic Wall Clock
Oct 15, 2009 | Heating & Cooling
May 28, 2009 | Heating & Cooling
Mar 09, 2009 | Cisco PIX 515E Firewall
Jun 15, 2008 | Samsung AS18A6RB Air Conditioner
26 people viewed this question
Usually answered in minutes!