Question about Heating & Cooling
On some of these, the filters are located outside of the actual unit in the silver metal duct that attaches to the bottom half of the furnace. It has a 1" cut into it where the filter just slides vertically into place. If you need additional help, call Weather King directly at (479) 646-4311.
Posted on Sep 12, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Hello, First thing is verify if you are getting voltage to the motor at the low speed motor terminal tat he control board and neutral. if you have voltage, next step is to check the capacitor, Discharge it and use a meter to verify the microfarad rating, if it is too low replace the capacitor. If that checks out good then the motors windings are either open or shorted to ground and must be replaced. If you don't have voltage at the control board then the board must be replaced.
Posted on Mar 05, 2011
Tips for a great answer:
Sep 23, 2013 | Rheem Ruud Weather King Corsaire Rheem...
May 18, 2011 | Weather King 12AJA4801AH Air Conditioner
Mar 05, 2011 | Heating & Cooling
Jan 12, 2010 | Weather King Heating & Cooling
Jan 17, 2009 | Weather King 12AJA4801AH Air Conditioner
Jan 06, 2009 | Weather King 12AJA4801AH Air Conditioner
Nov 30, 2008 | Weather King 12AJA4801AH Air Conditioner
Nov 15, 2008 | Weather King Heating & Cooling
280 people viewed this question
Usually answered in minutes!