Question about Heating & Cooling
You will need to check the contact on the outside unit, more then likely the relay is not pulling in or the fan motor is not working. When you up the panel it should be a black square with L1 L2 L3 and T1 T2 T3 the Ls are you lines you should have voltage if not then the breaker/fuse is off/bad. if you have voltage you should have the same on top, if not then the contact is bad if it is not pulled in. you can push it in and if should start the fan and compressor. You will also need to check for the 26 volts on the contact as this is what pulls/calls for the unit to work. hope this helped tim
Posted on Sep 09, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 06, 2017 | Heating & Cooling
Apr 19, 2016 | Heating & Cooling
Apr 28, 2014 | Heating & Cooling
Jun 26, 2011 | Heating & Cooling
Jul 17, 2010 | Heating & Cooling
Jun 09, 2017 | Heating & Cooling
Jul 02, 2009 | Heating & Cooling
Jun 26, 2009 | Heating & Cooling
34 people viewed this question
Usually answered in minutes!