Question about Intermatic & Indoor/Outdoor Rain Tight Timer
Yes, just leave it and it will start to do its thing...you have it set up and now just let it go...
Posted on Sep 08, 2010
Testimonial: "Fast answer just awesome, what I need to make decision on the job as an electrical contractor. This is intense customer service!"
Make sure the clock is set to the right time. If the timer is clock is set and the on time is 7:00 pm, then it should be off before that. (past 7:00am). if all is correct, it should do it's job until the power fails. At which time you need to set the clock again.
Posted on Sep 10, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
yes u will, but u will have to make sure one of the motor wires are hooked up that way also, in case it has been moved, here is a link with the diagram u need
Posted on Aug 21, 2009
T103 has 120Volt clock motor, so we can wire this timer.
T103 timer is rated for 30 amps and 2horsepower and your blowers use 28 amps.
So we're getting close to max on the timer. Hopefully blowers won't all be started at one time since motors draw maximum amperage when they start.
However, you need 30 amp breaker and orange 10 gauge wire for that much amperage >> unless only one blower is turned ON at any given time.
Always match wire size, amperage of breaker and amperage of Load or it will trip the breaker.
If you put 30 amp breaker on size 10 wire it is good. But 30 amp breaker on smaller size 14 or 12 gauge wire is fire hazard.
Add a comment at any time, and I will respond
Look at the basics:
You have 2 cables.
One cable comes from breaker box.
Other cable goes to three 120V plugs (120V is same as 110V).
Each cable has black-wire, white-wire and bare-copper-ground-wire.
How to wire the timer.
Timer has 5 terminals: A 1 2 3 4
A) Cable from breaker box:
White wire from breaker connects to terminal A
Black-wire from breaker connects to terminal 1
B) Cable going to 3 plugs
Black wire to plugs connects to terminal 2
White wire to plugs connects to terminal A
Ground wires connect to green ground screw.
Terminals 3 and 4 are not used in this case.
Here is a wiring diagram that shows 120Volt from breaker box and 120Volt going to Load
Posted on Nov 27, 2010
Testimonial: "Great help quickly thanks"
Tips for a great answer:
May 07, 2013 | Intermatic T103R 120-Volt 40-amp Timer...
Oct 07, 2012 | Intermatic T104R 208-277Volt 40-amp Timer...
Jun 18, 2011 | Intermatic T103 Indoor 120-Volt 40-amp...
Jan 26, 2011 | Intermatic T103 Indoor 120-Volt 40-amp...
Dec 11, 2010 | Intermatic 24 Hour Mechanical Mechanisms...
Dec 02, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Nov 20, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Oct 25, 2010 | Intermatic T103 Indoor 120-Volt 40-amp...
Jun 25, 2009 | Intermatic T103R 120-Volt 40-amp Timer...
May 12, 2009 | Intermatic T103 Indoor 120-Volt 40-amp...
Dec 18, 2013 | Intermatic & Indoor/Outdoor Rain Tight...
592 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: