Question about Heating & Cooling
Does the compressor also run constantly? If it does, the problem with the outside unit may be a stuck contactor. You can remove the cover where the power goes into the outside unit and the contactor should be located near there. If it is stuck, turn off the power to the outside unit and tap the contactor to try to free it, depending on how bad the contacts look, or replace the contactor. As for the indoor fan, you could have a bad fan relay, if that is what your unit has, or a bad fan sequencer, which is what some units use. These components will be located in the air handler. Hope this helps. Let me know what you find if this doesn't help and I can offer more advice based on that.
Posted on Sep 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 07, 2016 | Intertherm Heating & Cooling
Sep 24, 2014 | Heating & Cooling
Aug 26, 2011 | Carrier 38CKC036 Air Conditioner
Aug 22, 2010 | Dometic Rooftop RV Air Conditioner
Mar 31, 2010 | Goodman CLQ36AR49 Air Conditioner
Oct 10, 2009 | Heating & Cooling
Jul 22, 2009 | LG Heat cool Window Air Conditioner
Jun 03, 2009 | Heating & Cooling
Jul 20, 2008 | LG LWHD1800R Wall/Window Air Conditioner
550 people viewed this question
Usually answered in minutes!