Question about Heating & Cooling
Hello take a evap coil split (return temp vs supply temp) 18*F would be great.If it is lousy the TXV valve is restricting the flow of freon or the filter drier is clogging.Adding freon will overcharge the system and the suction will NOT improve.
Posted on Sep 08, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 05, 2015 | Heating & Cooling
Jun 24, 2014 | Ruud Central System Air Conditioner
Feb 24, 2013 | Scotsman Ice Maker CM3 30inW Cubed Ice...
Jul 15, 2011 | Heating & Cooling
Jun 08, 2011 | Heating & Cooling
Aug 09, 2010 | Amana Heating & Cooling
Jul 02, 2010 | Weather King 10AJA6001AH Air Conditioner
Jan 22, 2010 | Heating & Cooling
Aug 12, 2009 | Heating & Cooling
Jul 28, 2009 | Heating & Cooling
May 23, 2018 | Heating & Cooling
May 23, 2018 | Coleman Heating & Cooling
86 people viewed this question
Usually answered in minutes!