Question about Heating & Cooling
A little heat very carefully directed from a torch will soften the plastic and also will break the platic loose from the metal....then carefully with an awl pick the plastic out of the threads of the metal....this is tedious work and impatience will come back to bite you, so make sure to take your time and so not overheat or the metal will melt out of the plastic tray....but I have already repaired a mess by siliconing a new adapter into the tray with no threads....:-) when fixing up somebody else's mess....
So a little heat and a whole lot of pickin will git it for you....sounds like a bluegrass concert... :-)
Posted on Sep 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 15, 2012 | Ruud UBHC Air Conditioner
am a certified HVAC Technician. I have worked in the field since 1996. I have
seen this hundreds of times, if not a thousand times, in the past. Every
central air conditioning and heat pump system comes with TWO drain pans, The
MAIN drain pan is located within the AIR HANDLER (blower) UNIT, while the
EMERGENCY DRAIN PAN is extremely LARGE and sits under the ENTIRE AIR HANDLER
(blower) UNIT. The ONLY time water will be INSIDE an EMERGENCY DRAIN PAN is
when the MAIN DRAIN PAN condensate drain line is CLOGGED, causing the MAIN
DRAIN PAN to overflow. What causes the drains pans OR the drain lines to become
clogged is slime and scale from the condensate water as well as debris from
within the attic that may have either been blown by the air or may have simply
have fallen into the emergency drain pan; or some insects from the out of doors
have traveled up into the PVC Drain line and built a nest on the downward side
of the P-trap. The P-trap is designed to prevent critters from entering your
home through the PVC drain lines. Most CLOGS occur at the P-TRAP location.
The BEST thing to do is:
Locate the WHITE PVC drain pipe outside your house and ensure there is NO water
draining from it.
2. Locate the same WHITE PVC drain pipe inside your house. You should notice a "TEE" where two WHITE PVC drain pipes merge into ONE WHITE PVC drain pipe.
the below steps, in the order shown:
A. FIRST, find another person to act as your second set of eyes at the end of the WHITE PVC Drain Line that is located outside of your home. That person will be looking for water or debris to EXIT the end of that WHITE PVC DRAIN LINE.
SECONDLY, locate the WHITE PVC "P-TRAP" inside your house. It is
normally located within a couple to three feet of your indoor air handing
C. THIRDLY, very gently lift the entire WHITE PVC drain line up in the air as high as you can without breaking it, and slam it down onto the rafters or attic floor or garage floor. You are attempting to dislodge the CLOG within the drain pipe WITHOUT having to actually CUT the PVC and without damaging or breaking the WHITE PVC. Depending on how old the system is, it may or may not be brittle; and it may not take much to damage or break the PVC, which will cause leaks. So, be very careful at this point.
Ask the person outside if anything has started to EXIT. You can ALSO usually
hear water start to drain if you put your ear up to the drain line. If the
person said "NO"and if you don't see the water level getting LOWER in the
EMERGENCY drain pan, then REPEAT step "C" above.
If the person informs you that there IS water now starting to exit the WHITE
PVC DRAIN PIPE, you should then wait until all water has drained from the
EMERGENCY DRAIN PAN; and then pour at least 1 quart of BLEACH down that drain,
from the EMERGENCY DRAIN PAN exit. The BLEACH will further clear out any SLIME
which may be remaining within the "P-TRAP" and will also CLEAN OUT and
DISINFECT that drain line.
If the above steps do NOT work for you, then prepare to go into the next LOGICAL phase of your attack. Please NOTE: I am limited to 10,000 characters in my response, so I'll repost additional STEPS in another RESPONSE. Good Luck!!!
Sep 05, 2012 | Goodman CLQ36AR49 Air Conditioner
Sep 04, 2011 | Heating & Cooling
Jul 13, 2011 | Goodman GMS90703BXA Heater
Jun 19, 2011 | Heating & Cooling
Aug 23, 2010 | Carrier Heating & Cooling
Jul 19, 2010 | American Standard Heating & Cooling
Jan 11, 2010 | Goodman Heating & Cooling
Sep 13, 2009 | Heating & Cooling
26 people viewed this question
Usually answered in minutes!