Question about Goodman CKL42AR42 Air Conditioner
I'm new at this and I can't tell how old the post is but I'll contribute anyway.
You probably have fixed the problem by now. I wonder what part of the system is freezing up. I don't have a lot of experience but I know you can get frost where there is a restriction in the freon. If the freon line filter near the outside unit has frost on the house side the filter is partially plugged. I have also seen fost on the evaporator (attic "A" coil) when there is a shortage of return air flow. You could have a plugged filter or colapsed return duct, or even an "A" coil with a lot of dust covering and plugging the fins. I guess restrictions in your room air supply registers could cause the problem too. Maybe you have most of the vents closed off to save energy. Just some possibilities.
Posted on Oct 31, 2012
No you can not use a R-410 air handler with a R-22 condenser unit...the exspansion devices are different as the properties of the refrigerants are enough different that they are not interchangable...
Really your only choice is to replace the whole unit as it sounds like the exspansion valve or the orfice is partially clogged and it makes you constantly freeze up....
There are some things you could do to make it work at reduced capacity but it is way beyond what I could tell you through a computer...
Posted on Sep 08, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 25, 2013 | Cars & Trucks
May 25, 2011 | Amana Heating & Cooling
May 05, 2011 | Weather King 10AJA6001AH Air Conditioner
Aug 30, 2010 | Ruud Heating & Cooling
Aug 25, 2010 | Carrier 38CKC036 Air Conditioner
Jun 18, 2010 | Heating & Cooling
May 20, 2010 | Fujitsu Heating & Cooling
Dec 10, 2009 | Ruud UAMB Air Conditioner
May 11, 2009 | Heating & Cooling
Apr 23, 2009 | Heating & Cooling
170 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: