Question about Carrier 38CKC036 Air Conditioner
The one side of the contacotr in the condenser electrical box is welded closed...
Here is a tip about troubleshooting your air conditioner...
There are many things that can cause your air conditioner not to cool…
Air Conditioner Trouble - Review the Possibilities
Posted on Sep 08, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Sep 02, 2017 | Carrier Heating & Cooling
Jan 15, 2015 | Carrier Heating & Cooling
If it is just the condenser fan that means you have a fan relay that has welded shut. Turn power off to your unit and trace the wires from your condenser fan back into the control panel at the unit. You'll have 3 wires going to it. 2 go to the run capacitor and one goes to the fan relay. The one that goes to the fan relay is the part that needs to be replaced. If you have no fan relay and it goes to the main contractor, half of your main contractor is welded shut and will need to be replaced.
Sep 18, 2014 | Carrier 52PQ-515---3 Premier Series Heat...
Sep 23, 2013 | Carrier Packaged A/c 3 Ton 13 Seer And...
Jan 22, 2013 | Humidifiers
Oct 08, 2010 | Carrier Heating & Cooling
Sep 08, 2010 | Carrier 38CKC060 Air Conditioner
Jan 21, 2010 | Carrier Heating & Cooling
Oct 10, 2009 | Heating & Cooling
Jul 09, 2008 | Carrier 38CKC042 Air Conditioner
Jun 25, 2014 | Carrier 38CKC036 Air Conditioner
Jun 13, 2014 | Carrier 38CKC036 Air Conditioner
261 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: