Question about Sanyo STW1523H2 Thru-Wall/Window Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
ok, on these units, if by high side line you mean the small tube going from outside to inside, that tube is actually on the low side, the metering device is in the outdoor unit. If you shut the unit down, let everything thaw then restart and find that small tube is freezing up right at the outdoor unit right away, my guess is its low on charge. I see that you put some in, make sure it is the right knid of refrigerant. they do not hold alot. Where is your suction pressure running. If you put 2 to 3 pounds with no change, you may have overcharged but that is telling you that there is a restriction in the line inside the outdoor unit, probably the filter if it has one, or the metering device itself. Let me know what you find.
Posted on Jun 18, 2009
SOURCE: I have RCS-2HS4E sanyo air
the icons are;
snowflake = cool
raindrop = dehumidification
fan-blade = fan
sun = heat
I am assuming that you have it on the snowflake,hope this helps Tim
Posted on Apr 27, 2011
The condensate drain line was not properly installed. Make them pull the wall unit and correct the problem.
Be persistant until you are satisfied they have the problem corrected. Do not pay any additional money. If they do not correct the problem then report them online to the state board of heating and air. Fill out their requested complaint form and follow thru with a second complaint if you do not get total satisfaction from the contractor that installed the unit.
Hope this helps.
Posted on Sep 23, 2011
Tips for a great answer:
Jan 07, 2016 | Sanyo 24KS72 Split System Air Conditioner
Apr 21, 2017 | Heating & Cooling
Jan 02, 2011 | Sanyo Heating & Cooling
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Nov 04, 2008 | Heating & Cooling
Jul 30, 2008 | Heating & Cooling
51 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: