Question about MGE UPS Pulsar Evolution 1100 UPS System
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Check the big white battery power connector to make sure the metal tabs are making a connection to the female connection when pluging in the battery to the ups. If the tabs are not aligned the battery is not making a connection to the ups and will not engage the relays in the unit. Again check the metal cennections in the male connector to make sure the flat tab is aligned with the female plug when connecting the plugs together. I could not get my ups to power up and the reason was because when I connected the battery the tabs in the plugs were not making a connection and the ups was not getting the voltage from the battery that it needed to power up the relays. I checked everything in the ups and then I looked closer at the battery connector to make sure the ups was getting the power form the battery and it was not electricaly connected to the ups because of the large white conector tabs were not aligned to connect to each other.
Posted on Nov 27, 2011
Tips for a great answer:
Nov 27, 2014 | MGE Evolution 850 VA Tower UPS UPS System
May 05, 2011 | MGE UPS Pulsar Evolution 500 UPS System
Feb 18, 2011 | MGE UPS Pulsar Evolution 3000 XL (89349)...
Sep 29, 2010 | MGE UPS Pulsar Evolution 800 UPS System
Sep 15, 2010 | MGE UPS Pulsar Evolution 1500 UPS System
Jul 01, 2010 | MGE UPS Pulsar Evolution 2200 UPS System
May 17, 2010 | MGE UPS Pulsar Evolution 1500 UPS System
Aug 13, 2009 | MGE UPS Pulsar Evolution 3000 UPS System
102 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: