Question about Amana Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
be aware that not repairing this asap that you are causing yourself more problems First I would change out the fan capacitor and see if this could be the problem. Secondly if the capacitor isn,t the problem change out the motor . By continuing to allow the system to cycle like this the compressor will take a dive on you costing more . Good Luck
Posted on Aug 04, 2009
Testimonial: "Yes, it's dual run capacitor problem. I used a stick to spin the fan blades and it starts to slowly spin and up to normal speed, so motor is good."
Does the motor data plate say anything about the motor. You can hook up a motor like yours with 3 wires. First use an ohmmeter and check the resistance between the brown/white wire to the black then the yellow wire. The resistance between brown/white and one of the others should be pretty much 0 ohms. If not check between the brown wire and the black and the yellow. Which ever wire has 0 ohms with the brown/white wire is the common leg. You can put a wire nut on the brown/white, it will not be used. Next the brown should be for the start winding and the other wire left over will be the run winding. Then connect the common to L2. L1 will go to the run winding and one side of the capacitor and brown will go to the other side of the capacitor. I hope this isn't too confusing. Let me know if I need to explain it better.
Posted on Jun 09, 2010
Testimonial: "Thank you very much for your help-I had the motor leads reversed and when I placed the brn/white to the common on cap like someone else had instructed it of course shunted out and blew the fuses in the disconnect. I used my meter(duh) and switched the motor leads. We got air!! THANK YOU!"
Tips for a great answer:
Apr 09, 2013 | Amana Refrigerators
Jan 24, 2012 | Weather King 10AJA3601AH Air Conditioner
Dec 13, 2009 | Amana PTC074B25AE Electric Heat Air...
Oct 11, 2009 | Dometic Rooftop RV Air Conditioner
Sep 13, 2009 | Amana Heating & Cooling
Aug 04, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 28, 2009 | Amana PTH123B25AJ Heat Pump Air...
Jun 28, 2009 | Heating & Cooling
May 06, 2009 | Heating & Cooling
210 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: