Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: no heating from Mr slim
P8 refers to outdoor protection device activation usually caused by low gas charge or blocked condenser coil. any good a/c company can resolve this for you. however please note that if it is gas related a pressure test must be carried out to determine where that potential leak may be and that can be very costly.
Posted on Nov 14, 2007
no sir gary,
the water would not go to the drain pan if you install it vertically.
water would just drop anywhere and would ruin a lot of things...
tnx 4 using fixya,
Posted on Sep 13, 2008
If you have any experience in working with electrical systems, you can, but if not you should call a service technician.
First being very careful, check to make sure contactor is engaging.
Then check to see if you have the same voltage across all three wires on the compressor side of the contactor, assuming this is 230 volts, check T1 to T2 should have 230 volts, then check T2 to T3 should have 230 volts then check T1 to T3 should have 230 volts. If you have 230 volts to all 3 wires then the compressor is bad probably an open winding and needs replaced. Before replacing the compressor you need to check the resistance (with an ohmmeter) between all 3 terminals at the compressor. In order to do this you need to disconnect all power to the unit and ohm the compressor terminals from T1 to T2, T2 to T3 and T1 to T3 they should all have the same resistance if they do then the windings are good and the compressor is locked up, if one of the the windings is different then the windings are bad, either way the compressor needs replaced.
Posted on Nov 10, 2009
Tips for a great answer:
Sep 24, 2013 | Mitsubishi Mr. Slim MXZ30TN Air...
Nov 10, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Sep 18, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Jul 15, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
May 27, 2010 | Mitsubishi Mr. Slim MXZ30TN Air...
Jul 09, 2009 | Heating & Cooling
Jun 10, 2009 | Dometic Rooftop RV Air Conditioner
Jun 10, 2009 | Heating & Cooling
122 people viewed this question
Usually answered in minutes!