Question about Goodman PHKJ048-1 Air Conditioner
It seems to me that your suction should be @ 76 or so. 52 is low. the coil will ice up with any suction PSI below 58. Disconnect the unit from the duct work and make sure there is no restriction in the duct size. In other words. Does the unit work properly with out the duct? I find most mobil homes have a restriction in the amount of return. A 5 ton split needs a 20 inch round return. You never see this size return on a package unit. Does the return **** the filter in? I have had to add returns to large mobil homes because there just not designed right.
this is only a possibility. Is the temperature split on the equipment between 18 and 20 If it is then I don't thing you have an equipment problem. Also make sure there are no holes in the duct work.Last one I had unit was working fine but the duct work had a big hole in it from some animal under the trailer.
Posted on May 18, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 16, 2012 | Goodman Heating & Cooling
May 01, 2011 | Heating & Cooling
Feb 21, 2011 | Goodman CKL36AR36 Air Conditioner
Dec 16, 2010 | Heating & Cooling
Sep 03, 2010 | Goodman Heating & Cooling
Aug 14, 2009 | Weather King 10AJA6001AH Air Conditioner
Aug 07, 2009 | Goodman CLQ36AR49 Air Conditioner
Oct 07, 2008 | Goodman Heating & Cooling
Aug 16, 2008 | Goodman GMS90703BXA Heater
Jul 29, 2008 | Heating & Cooling
Dec 11, 2011 | Goodman PHKJ048-1 Air Conditioner
260 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: