Question about Amcor ALTL-12000E Portable Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: fan runs constantly on cool mode
Simple Question: Did you check to see if the fan switch on the
t-stat is in ON or AUTO? If ON the fan runs nonstop. If in auto the fan cycles with the outdoor unit.
next does the fan shut off if you turn the t-stat to off?
A stuck relay should keep the fan running all the time.
Sometimes if the relay is stuck you can whack the side of the Air Handler and the connection will break.
Sometimes instead of a relay there is a stack switch.
It's a little black stack of 3 disks this is a bi-metal switch.
they do get stuck more often than relays.
The fan relay may be on a electronic board. I don't know for sure without seeing your unit.
Good Luck Phil
Posted on May 20, 2008
If the unit was set up a week ago the technician should warranty his work and come back and take care of the problem for you, not knowing what was set up and how, it's hard to say if it's a problem with the unit or the control (t'stat or programming if it's a programmable t'stat).
Posted on Mar 17, 2009
SOURCE: air is not cold
the fact that the compressor light is coming on tells me power is being sent to the compressor.
if that is true then there is really only 2 possibilities.
1) you have a wire (or maybe 2) burnt away from the terminal(s). To repair this is fairly simple for the service tech but somewhat complex for the inexperienced, so I won't go into here - but if this is the problem you can probably (with a little expert help) fix it yourself.
2) the compressor is not starting even though voltage is being applied to it's terminals. Usually this is caused by the compressor being 'electrically open,' and there is nothing that can be done except to change out the compressor.
Posted on May 05, 2010
Tips for a great answer:
Oct 17, 2015 | Thermostats White Rodgers 1F80-261...
Jul 21, 2015 | Dometic Rooftop RV Air Conditioner
Nov 10, 2012 | Sharper Image Drink-O-Matic
Aug 26, 2012 | Cadillac DeVille Cars & Trucks
Aug 26, 2011 | Dell Inspiron 530 Desktop Computer
May 03, 2017 | Heating & Cooling
Jan 20, 2011 | Heating & Cooling
Aug 17, 2009 | LG Art Cool LA1000PR Air Conditioner
Jan 06, 2006 | Panasonic PT-40LC12 40" Rear Projection...
Jul 06, 2014 | Amcor ALTL-12000E Portable Air Conditioner
30 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: