Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
This indicates the the 2 installed temp sensors are having a reading the is more than 2 degrees in difference. It is either a failed sensor, or one of the sensors is not fit snuggly into the header.
To test a sensor, turn your multimeter on OHMS or RESISTANCE and connect probes to each wire. at 80 degrees, the sensor should read 93 OHMS. At 70 degrees it should read 118 OHMS
at 60 degrees it should read 153 OHMS
Posted on Oct 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 26, 2011 | Raypak Free Hydraulic Lift Gate Delivery -...
Jan 01, 2011 | Rheem M206A 206K BTU Pool and Spa Propane...
Dec 06, 2009 | Balboa Instruments Garden
Jul 16, 2009 | Raypak Free Hydraulic Lift Gate Delivery -...
Jun 19, 2009 | Raypak Free Hydraulic Lift Gate Delivery -...
May 24, 2009 | Raypak Free Hydraulic Lift Gate Delivery -...
323 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: