Question about Goodman Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: How do I clean the
Remove the cover in front of the coil, If the line set runs thru this cover try to slide it out of the way, some units have a triangle shaped sheet metal covering the end of the coil, if so remove.
The dirty side of the coil will be, on the air filter side of the coil, if the coil is very dirty use a vacuum with a with a brush and vacuum off the worst of the debris, some fins are soft so pay attention to them along the process. Using something like 409 and a pump up sprayer or squirt bottle spray the coil, start at the bottom and work your way up, this is so the water will drain into the drain pan.
When using the 409 and water watch that the water is not dripping into the furnace if so use a towel and or something to prevent the drips from getting into the furnace, take your time and be thorough.
Please buy a quality air filter, and prevent having to clean the coil again.
Posted on Jul 12, 2011
Tips for a great answer:
Mar 08, 2016 | Goodman Heating & Cooling
Apr 11, 2014 | Goodman Heating & Cooling
Aug 26, 2013 | Heating & Cooling
Aug 04, 2012 | Goodman CKL36AR36 Air Conditioner
Dec 09, 2010 | Goodman B1859005 Induced Draft Blower...
Sep 01, 2010 | Goodman CKL42AR42 Air Conditioner
Oct 06, 2009 | Goodman GMS90703BXA Heater
Aug 14, 2009 | Goodman Heating & Cooling
144 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: