Question about Heating & Cooling
The condensate line from the coil must be blocked. Use compressed air to clear the lines. Or possibly a crack in the condensate pan where the fitting goes in or not sure if it is old enough but the older coils had steel condensate pans that will rust through
Posted on Sep 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 19, 2015 | Heating & Cooling
Jun 16, 2011 | Heating & Cooling
Apr 29, 2011 | Heating & Cooling
Aug 23, 2010 | Heating & Cooling
Feb 04, 2010 | Heating & Cooling
Sep 23, 2009 | Ruud UBHC Air Conditioner
Aug 11, 2009 | Heating & Cooling
Jul 29, 2009 | Heating & Cooling
460 people viewed this question
Usually answered in minutes!