Question about Raypak Rp2100 Pool & Spa Heater Lonox 407k Btu Natural Gas Polymer Header Digital Rp407aenc
If this is a MV heater you need 500MV to run the heater. 200 to start the pilot and 300 to open the main valve. If your dropping 100MV on the safty circut you will need 600 or better to fire the heater. I would clean all the connections on the safty circut. I will usually change the whole pilot assembly, but you can get away with just the pilot generator.
It's hard to say how to remove the pilot as their are a couple of different ones and the heater you have listed has none, but a hot surface ignitor instead. Also it runs on 110 or 220v stepted down to 24v for most of the safty circut.
Posted on Sep 05, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 16, 2014 | Raypak 206A Digital ASME Natural Gas IID...
Jun 01, 2014 | Raypak Pool & Spa
May 14, 2014 | Raypak Free Hydraulic Lift Gate Delivery -...
Sep 12, 2013 | Jandy Lite 2 Natural Gas Pilot Light...
Aug 17, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Aug 06, 2013 | Raypak Pool & Spa
May 28, 2013 | Raypak Pool & Spa
Nov 11, 2012 | Raypak Free Hydraulic Lift Gate Delivery -...
Aug 27, 2011 | Raypak Versa Pool Heater Gas 55000 BTU...
232 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: