Question about Honda Transfer Kit for EU 3000iSAC and EB 3000CKAG
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Generator output
Hi, You don't say whether this is under load or not but if not is within the acceptable range, which is +/- 10% . Generally speaking, voltage on a generator is not the issue but the load which it will carry, hence their wattage ratings. Measure your household voltage and you will see that it varies from day to day but usually stays within the limits and your electrical panel is rated in amperage. Hope this answers your question!
Posted on Feb 08, 2009
At the controller, you need to see if it is actually sending electricity out of the Generator/Alternator, have a look where the leads from the power making unit mates, (Think of it as a motor in reverse) onto the board. There should be an AC Voltage there, then, work back, or out from there, trace the Voltage until it stops, thats the problem... Check the Breaker isn't tripped or faulty too.
Posted on Mar 22, 2010
Those voltage readings MAY be normal.
The AC waveform may cause your meter to read inaccurately. You would need to use a TRUE RMS meter to accurately read the voltage.
The siple meters actually read the AVERAGE voltage and then are calibrated to mulltiply it by the "form factor" for a sine wave. OFTEN these generators don't produce a clean sine wave. A square-ish wave will read higher on the garden variety meters.
Compare the brightness of a lamp comparing to when run on your utility.
The frequency depends on engine speed ... yours is running a bit fast...check it under at least half load and if off, adjust the govenor slightly.
Posted on May 02, 2010
Testimonial: "Still working on the problem but tips were a real help."
Tips for a great answer:
Sep 21, 2014 | NEC Mitsubishi MGE 4000 Generator ROU...
Sep 17, 2011 | Pramac Commercial 3100 Watt Honda ...
Apr 28, 2011 | Miller Trailblazer 302 Welder Generator...
Feb 20, 2011 | NEC Mitsubishi MGE 4000 Generator ROU...
Dec 22, 2009 | Electrical Supplies
Sep 25, 2009 | Honda Electrical Supplies
Sep 24, 2009 | Northstar Generator 18 Hp, 10,000 Watt,...
Jul 04, 2009 | Yamaha 4500 Watt Electric Start Generator...
420 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: