Question about Heating & Cooling
Hi, Chris, this is the thermostat for sure. It has a built in sensor on the circuit board that gives the stat the command to do what its supposed to do. From what you are saying, it has to be the stat. Be sure you mark the wires on this stat, if you have a gas furnace with this central unit, the stat will have markings at the terminals like this, Red wire to either the Red R/C, or R/H with a jumper across the 2, a W, white for heat, Y yellow for cooling circuit, and G green for the fan control. The new stat will come with the red jumper installed for you. Now, if you have a heat pump, the terminals will have more wires such as a R, O, B, W, W-1, Y, G, C, and so on. Heat-pump wiring is much more difficult to install the stat as it has to have the same terminals and if they are not terminated right, you will have problems. You may want a pro to wire it in for you only if you have a heat-pump. If its just a standard stat like I 1st said, turn off the breaker and it is simple to install. The voltage is only 24 volts ac. Please don't forget to rate me Chris as I know you will be kind, and I will also be checking in on you to see how it is going. You can also contact me if you need more help by my user name below.
A/C, Heating, & Refrigeration Contractor.
Posted on Sep 03, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2015 | Goodman Manufacturing Goodman GPH1348M41 4...
Aug 12, 2017 | Amana Heating & Cooling
Aug 17, 2012 | Honeywell Programmable Thermostat Heater
Sep 26, 2011 | 1965 Ford Mustang
Oct 23, 2010 | Heating & Cooling
Oct 12, 2009 | Heating & Cooling
Mar 27, 2009 | 1988 Cadillac Sedan DeVille
Mar 11, 2009 | Coleman Heating & Cooling
Dec 06, 2008 | Heating & Cooling
Jun 24, 2008 | Honeywell Heating & Cooling
27 people viewed this question
Usually answered in minutes!