Question about Heating & Cooling
Hi, it sounds as though you have a faulty thermostat that failed before your eyes. The circuitry in the sub-base has failed. If the stat is set in the off posistion and you turn the fan switch on, just the fan will run. If it is on cool and you turn the fan to on and not auto, it should bring on the compressor. You will need to get a new thermostat. Kill the breaker and remove the cover to the stat and expose the wiring. This is a 24 low voltage stat. It will have terminals rh and rc with a red jumper connecting the 2, and your red hot wire connected to either one.Y, yellow for cooling, G, green for fan control, and white , W for heat control. Y yellow may be using a blue wire instead. They sometimes do this. Write this down and pick up a stat at Home Depot, Lowe's hardware This will solve your problem. Please don't forget to rate me as I know you will be kind. I will check in on you as I keep files on all of problems I have solved to help people. You can also get back to me by my user name below.
A/C, Heating Contractor
Posted on Sep 03, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 04, 2016 | Heating & Cooling
Aug 24, 2014 | Honeywell Th5220d1003 Non-programmable...
Nov 29, 2013 | Heating & Cooling
Jun 20, 2011 | Heating & Cooling
Dec 04, 2010 | Heating & Cooling
Aug 02, 2010 | Nor-Lake KLF7766C Commercial Freezer
Jul 07, 2010 | Honeywell Electronic Programmable...
Nov 11, 2008 | Honeywell Programmable Thermostat Heater
May 09, 2008 | Honeywell Electronic Programmable...
118 people viewed this question
Usually answered in minutes!