Question about LG Heating & Cooling
SOURCE: lg ductless no ac
I may not be of much help but I may be able to guide you into some diagnosos. If there is a communication problem between the inside and outside unit, both on the inside and outside units a colored LED will bling 5 times then pause for 3 seconds. The 33 and 44 codes are confusing to me because I have never seen this. Try resetting the outside unit with no call for heat or cool from the inside unit. After about 20 seconds, restore power to the outside unit. Go in and turn on the remote and make sure you lower the cool setting more than degrees cooler than the room temp. After 3 minutes the outside unit should turn on. If you get an error code of either 1, 2 or 5 blinks document it for the technician. If you continue to get your 33 and 44, you have a bad control board. If all else fails, press and hold the button located on the lower left side of the art unit and hold for about 5 seconds. If it still no longer works, now you will need the help of someone who knows these units.
Posted on Sep 09, 2007
One thing you need to check is Polarity. the 2 wires red and white, need to be on the same terminals inside as they do outside. this is very important.
Posted on Oct 28, 2009
That means that the unit needs servicing, try cleaning the outside coils and cleaning the filter on the inside unit.
Don't forget to rate this post!!
Posted on Oct 01, 2010
Tips for a great answer:
Jul 10, 2015 | Fujitsu ASU9RLS2 Single Zone Wall Ductless...
Jun 04, 2015 | Carrier Heating & Cooling
Jun 18, 2014 | Samsung AQV36JA Classic 36000 BTU Single...
May 26, 2014 | LG LMN127HVT LMN127HVT 12 000 BTU Ductless...
May 01, 2009 | Carrier 36KCARMS Air Conditioner
Mar 07, 2009 | Soleus KFR12GWD 12,000 BTU Heat & Cool...
Feb 11, 2009 | Heating & Cooling
Dec 13, 2008 | Fujitsu 18C1 Air Conditioner
Sep 08, 2007 | LG Art Cool LA121CNP wall/window Air...
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: