Question about Kitchen Appliances - Others
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Some one missed the wiring diagram. I believe its like this:
L1 = Line 1 = (Hot all are same thing)
Now usually the black is for AC and connects to a normally Open (NO) contact on the blower relay.
The heater speed (either red or blue) go the the normally Closed (NC) on the blower relay and on one side of this wire or contact on the relay it goes to the heating blower thermostat on the furnace.
The remaining wire (blue or red) you tape off.
L1 also feeds the Run Capacitor on 1 side and the Brown wire feeds the opposite side
The white wire is Neutral and goes to the neutral on the main line.
If this helps you please rate me accordingly and good luck.
Posted on Mar 13, 2009
Tips for a great answer:
Dec 21, 2014 | Fasco Intercity Heil / Tempstar Furnace...
May 13, 2014 | Goodman Heating & Cooling
Jun 28, 2013 | Water Heaters
May 26, 2011 | Goodman Furnace Draft Inducer Blower ...
Apr 27, 2011 | Heating & Cooling
Apr 01, 2011 | Fasco Centrifugal Blower 115v
Mar 13, 2009 | Kitchen Appliances - Others
Jan 04, 2009 | Cross Furnace Draft Inducer Blower 115...
79 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: