Question about Heating & Cooling
It may not help but it sounds like the tech took a control wire for the cooling circuit loose at the indoor air handler/furnace so that he could bring the heat on to check it, and forgot to hook it back up. That may not be the case, but if it is it wouldn't be the first time. Due to the possibility of electrical shock, and the uncountable number of system configurations I wouldn't be able to tell you how to check it. Even the best tech's make mistakes, and if they have any integrity they won't charge to come back to fix.
Posted on Sep 02, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 03, 2011 | Heating & Cooling
Jun 07, 2011 | Heating & Cooling
Nov 04, 2017 | Heating & Cooling
May 23, 2010 | Goodman CKL24AR24 Air Conditioner
Aug 15, 2009 | Heating & Cooling
Jun 04, 2009 | Heating & Cooling
Apr 27, 2009 | Heating & Cooling
55 people viewed this question
Usually answered in minutes!