Question about Weather King Heating & Cooling
It sounds like maybe the fan is not coming on outside but the compressor is running and just tripping on internal heat protection .... Please turn power off to the outside unit and let cool for 15 minutes then remove electrical compartment cover and see if the contactor is pulled in.. if its pulled in then look at the capacitor that is usually sulver and round with wire terminals on top.. it should be flat on top and not rounded.. if its rounded then replace it by ordering part online or contacting locar electrical parts company or if none of this looks to be the problem please contact a local a/c repair company.
Posted on Sep 01, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 11, 2015 | Heating & Cooling
Aug 03, 2011 | Goodman CKL49AR49 Air Conditioner
Jun 06, 2011 | Heating & Cooling
May 11, 2011 | Heating & Cooling
Apr 11, 2010 | Goodman CLJ36AR42 Air Conditioner
Jul 12, 2009 | Goodman CLQ36AR49 Air Conditioner
May 26, 2009 | Goodman CPLE24-1 Air Conditioner
Dec 04, 2008 | Heating & Cooling
Sep 01, 2008 | Bryant Heating & Cooling
Jul 23, 2008 | Heating & Cooling
27 people viewed this question
Usually answered in minutes!