Question about Heating & Cooling
Is this a split system or a wall unit. If it is a split system, is the outdoor fan running? If it isn't, check the fuses or disconnect first. If that's good, set the thermostat to make the air come on then remove the cover where the power goes into the outside unit and see if the contactor is pulled in. Next, check voltage on the primary and secondary side of the contactor and make sure it is getting power. If the outdoor fan is running then the problem may be just your capacitor. You can check it with a multimeter or take it to a heating and air supply and they can check it. If the capacitor is good then check the compressor motor windings. Let me know what you find and I can give more suggestions. There are a lot of possibilites but these are some common ones.
Posted on Aug 31, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jun 30, 2013 | Heating & Cooling
Aug 04, 2011 | Heating & Cooling
Apr 27, 2010 | 2003 Hyundai Santa Fe
Apr 04, 2010 | 2005 Daelim Daystar
Jan 22, 2010 | Plumbing
Jun 02, 2009 | Maytag MZD2665HE Stainless Steel Side by...
25 people viewed this question
Usually answered in minutes!