Question about Coleman Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: I have a trane xl80
The ignitor on your furnace broke... this is a common problem and not too hard to fix if you have a place to buy the ignitor from... it also can be purchased online...
If you are not confortable with repairing it then call a repairman...
Here is a tip that wrote about how to buy heating and airconditioning parts online.
How to find Air Conditioning, Heating and Furnace parts online.
Posted on Nov 30, 2010
SOURCE: Carrier Performance Boost 80 has
this indicates fault 33, on inside of access panel will tell you faulty switch. i believe off top of my head is pressure switch open, this a safety switch to verify that inducer fan is working, several things besides a failed part can cuase this, there is a rubber hose going from the inducer fan houseing to the safety pressure switch, remove hose from fan housing and run a small stick ,wire or torch tip cleaner, down the acces port, calcium builds up inside the port and blocks the sampling of pressure, reassemble and try it, if this works add it to yearly maintenance could need new switch or inducer fan motor, these need to be replaced by a tech, also birds can block flue pipe
Posted on Feb 02, 2011
SOURCE: The control board on my
What make/ model is your furnace? Do you have the wiring diagram to the unit? Usually on the inside of the heater panel on a split unit where the heater is in one location and the outside unit (condensor) is outdoors.
Posted on Aug 02, 2011
Tips for a great answer:
Nov 19, 2014 | Coleman Heating & Cooling
Jan 24, 2008 | Goodman GMS90703BXA Heater
Apr 13, 2014 | Carrier Furnace Control Board Bryant...
Aug 02, 2011 | Heating & Cooling
Jan 31, 2011 | Heating & Cooling
Apr 27, 2010 | Coleman Propane Forced Air Heater...
Apr 03, 2009 | Sears Craftsman LiftMaster Chamberlain...
Jan 15, 2009 | Heating & Cooling
90 people viewed this question
Usually answered in minutes!