Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
SOURCE: Need wiring diagram
check the capicitor if it is domed up on top bad check the wires at the compressor to see if burnt take a insulated object and bump the contactor in to see if comp starts if so then out on low voltage circ check for call from stat on common to yellow then follow the connections may be out on low psi switch located in the suction line
Posted on May 10, 2009
Hi, the outdoor unit will start to freeze when it is cold outside, but also it should go into a defrost mode to melt this ice either by the defrost board or defrost thermostat. You will know as steam will rise like smoke and some folks think it is on fire. If it never goes into defrost, get back to us and we can go through some things to check. Merry Christmas,
Posted on Dec 24, 2009
Tips for a great answer:
Aug 11, 2017 | Heating & Cooling
Jan 06, 2017 | Heating & Cooling
Jan 20, 2016 | Gibson Nordyne/2 Ton Heat Pump Package...
Aug 06, 2014 | Heating & Cooling
Feb 26, 2010 | Heating & Cooling
Nov 21, 2009 | Heating & Cooling
Sep 05, 2009 | York Yankees Bedding MLB Comforter
Dec 03, 2008 | York Yankees Bedding MLB Comforter
247 people viewed this question
Usually answered in minutes!