Question about Heating & Cooling
Hello 93 The compressor caused the breaker to trip.A weak capasitor or burnt wire is a common cause.It sounds like the compressor is NOT on even though the fan is.It may need a new wire or maybe a HARD START kit to help restore operation.Call for help.HS kits are not expensive.NO damage results from leaving it on, the problem would have happened anyway even if you went on vacation or not.The curcit breaker stopped it.Its worth fixing.
Posted on Aug 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get 2 Free calls (no credit card required) and instant help on almost anything you can think of (from cars to computers, appliances, handyman, and even pets).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 08, 2017 | Heating & Cooling
Aug 02, 2016 | Heating & Cooling
Jun 29, 2017 | Goodman GMS90703BXA Heater
Aug 13, 2011 | Heating & Cooling
Jul 10, 2010 | Heating & Cooling
Aug 08, 2009 | Heating & Cooling
525 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: