Question about Goodman CLQ36AR49 Air Conditioner
Sounds like you have the run wire connected to the capacitor instead of the start wire. I expect you have 3 wires; Common-black, Run-probably orange, and Start-brown. You should have either L1 or L2 from the contactor connected to the Com terminal of the capacitor. Connect Orange/Run to the Com terminal of the capacitor. Connect Brown/Start to the Fan terminal on the capacitor. Connect Black/Common to the other side of the contactor. The fan should run the other way.
Posted on Aug 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jul 02, 2011 | Amana Heating & Cooling
Jul 29, 2010 | Heating & Cooling
Jun 02, 2010 | Carrier 38CKC042 Air Conditioner
Sep 26, 2009 | Heating & Cooling
Jul 09, 2009 | Heating & Cooling
Jun 13, 2009 | Goodman CKL24AR24 Air Conditioner
Aug 25, 2008 | Goodman CKL60AR60 Air Conditioner
May 27, 2008 | Goodman CKL24AR24 Air Conditioner
Apr 20, 2008 | Carrier 38CKC036 Air Conditioner
87 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: