Question about Heating & Cooling
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You ether have an internal by-pass or an external one. If you have an external one you need to close it up to 80-90 persent. This will allow some water to go past the heater but most will go through it. If it is open too much the water will offer enough pressure to start the heater but if it doesn't flow through it. It will boil the water inside it and gurgeling and pounding as the water expands. If you have a problem with your internal by-pass you will get the same result but it is harder to fix. This is a disc mounted on a shaft held closed by a spring inside your water manifold on the heater. If you open the header you can get access to the by-pass and may be able to sand the shaft down or if the disc is broken you can replace it. Hope this helps and good luck.
Posted on Dec 20, 2009
hi. i have mini temp boiler 150 btu 5yers old . it is burning with know radiation .it is up to thempitio .but it will not shut off.flame is good radietor is hot ,help?
Posted on Jan 05, 2010
Tips for a great answer:
Dec 20, 2013 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 02, 2010 | Amtrol ST-120V-C THERM-X-TROL ASME...
May 15, 2010 | Heating & Cooling
Feb 11, 2010 | Teledyne Laars Laars Lite 2 Pool Heater...
Dec 25, 2009 | Lite On Laars Lite 2 Heaters: 250,000BTU...
Dec 17, 2009 | Garden
Nov 04, 2009 | Lite On Laars Lite 2 Heaters: 250,000BTU...
Oct 20, 2009 | Cozy (W352E) Heater
61 people viewed this question
Usually answered in minutes!