Question about Rheem 266K to 399K BTU Swimming Pool Natural Gas Heater ()
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
coud be several things, Do you have Gas and is gas toruned on. Is valve on. The Pilot could be dirty and need cleaned. $350+ sounds reallly pricy for a pilot assembly. Call your Gas Company and get an Estimate and a Qualifed Service tech. You may try turning Off the Power to the Heater Unit and turning it back on , and then trying to turn on heater again, So times after several atemps the valve will lock out and the power needs reset on Propane units.
Posted on Jun 29, 2010
Error Code ROL is "HEAT ROLL-OUT SAFETY SWITCH OPEN". The heater is equipped with a cutoff device to prevent flame roll-out in the event the heat exchanger becomes blocked. This is either a "manual reset", or "Single-use" type fusible link/thermal fuse, that must be replaced or reset after any over temperature conditions have been fixed. Excessive restriction in the heat exchanger flue passage may cause the switch to disable the heater. I don't know your exact model so I'm just generalizing. If you reset or replace the switch, and it trips/burns out again, then you need to address what is causing it. make sure the heater is cleaned out well and no debris is blocking the flue. I fthis doesn't help you can always try calling Raypak Service department at (805) 278-5300.
Posted on Sep 20, 2010
What is the serial number? The 337A series has only been around since the end of 2004 so it will be somewhere in the last 5 or so years.
Posted on Oct 27, 2010
Testimonial: "thanks. I'm selling it and the buyer wanted to know the manufacture year, and I couldn't find it anywhere on the rheem website. I appreciate your help"
sounds like you have a bad thermal governor (regulates water temp inside the heat exchanger) or your pH has been to high and your exchanger is completely scaled up.
Posted on Aug 18, 2011
Tips for a great answer:
Aug 04, 2014 | Raypak Rheem RP2100 399K BTU Natural Gas...
Oct 16, 2013 | Rheem 266K to 399K BTU Swimming Pool...
Aug 24, 2013 | Raypak Rp2100 Pool & Spa Heater Lonox 407k...
Aug 18, 2013 | Rheem 266K to 399K BTU Swimming Pool...
Aug 19, 2009 | Rheem Tankless Water Heater Manifold...
46 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: