Question about Goodman CLQ36AR49 Air Conditioner
Your description is possibly a bit vauge for the problem it could be, but starting from the compressor, question is "can you hear the compressor running"? If you can then switch off quickly and check the cooling fan capacitor. almost certainly it has popped.If it has, and even with a new capacitor it wont start, then a complete condensing fan unit is required.If the compressor isnt running, then one of a few things could be the problem. A- The voltage getting to the compressor or the cap, is not correct which points to a problem with the board. B- If the compressor is jambed,(siezed),then it is bringing the voltage down to the point where even the fan cant run. Need to check those points to determine the next course of action.
Posted on Aug 28, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 05, 2013 | Dometic Rooftop RV Air Conditioner
Apr 27, 2011 | Hitachi EC119SA Twin-Stack Air Compressor...
Feb 01, 2011 | Samsung AS18A6RB Air Conditioner
Jul 29, 2010 | Heating & Cooling
May 02, 2010 | LG LA185HV Split System Air Conditioner
Jan 25, 2010 | Heating & Cooling
Aug 12, 2009 | Heating & Cooling
May 30, 2009 | Bryant 463AAC005BA Air Conditioner
Dec 02, 2008 | Amana PTH123B25AJ Heat Pump Air...
189 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: