Question about Xantrex Technology Electronics - Others
Check you line out distribution leads for a system ground with the #2 inverter disconnected. Also chect across the line out terminals onthe inverter with the distribution leads disconnected. The inverters use a floating ground vs and installed ground. If the inverter senses a ground your will read 120VAC to ground on each output terminal bu\out will read ZERO across the two terminals. If you read 120VAC across the to terminals with the dristribution leads disconnected and lose that output voltage with the leads connected then you have introduced a FIXED ground into the system. You will need to isolate where the fixed ground manifested itself as a result of connecting the new water heater.
Thanks for choosing FixYa.
Posted on Aug 27, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
May 23, 2011 | Jandy Lite 2 Natural Gas Pilot Light...
May 16, 2011 | Garden
Mar 10, 2017 | Pentair Minimax NT Heater
Sep 05, 2010 | Philips Senseo HD-7810 Coffee Maker
Mar 01, 2010 | Reliance & 30 Gal LP Gas Water Heater
Jan 07, 2010 | RoadPro AC/DC Power Inverter 2000/5000w
Nov 22, 2009 | Noritz 6.9 Gallon Residential Direct Vent...
May 29, 2009 | Pentair Minimax NT Heater
Jan 19, 2009 | Pentair Minimax NT Heater
63 people viewed this question
Usually answered in minutes!