Question about Heating & Cooling
Hello Check the burner motor itself for a red button and see if that pooped up.
Posted on Aug 26, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 09, 2016 | Heating & Cooling
Feb 13, 2016 | Heating & Cooling
Nov 25, 2013 | Heating & Cooling
Apr 22, 2013 | Heating & Cooling
Jan 30, 2013 | Heating & Cooling
Mar 11, 2011 | Coleman Heating & Cooling
You need to find out if the problem is in the T-stat, T-stat wire or in the furnace you can do this in a few easy steps
Step 1- Unwire the low voltage from the furnace. Then turn the power back on and see if the blower comes on if it does then the problem is in the furnace and you will need to troubleshoot the furnace (see bottom of page for troubleshooting furnace) if it does not then proceed to step 2
Step 2- Wire the low voltage back up to the furnace (follow the wiring diagram below). And unwire the T-stat, make sure that no wires are touching each other, then turn the power back on to the furnace, if the blower starts then you have a short in the T-stat wire and you will need to pull a new wire. If it does not then proceed to step 3
Step 3- Turn the power back off at the furnace and wire the T-stat back up (follow the wiring diagram below). Turn the T-stat to auto heat 90 if the heat does not start but the blower just runs then you need to replace the T-stat.
Nov 24, 2010 | Comfort-Aire Heating & Cooling
Jan 04, 2009 | Honeywell Electronic Programmable...
Oct 30, 2008 | Carrier 38BRC048 Air Conditioner
Nov 29, 2007 | Honeywell Power Humidifier: Furnace...
17 people viewed this question
Usually answered in minutes!