Question about Goodman GPH1324H21A WallWindow Air Conditioner
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
That's what contactors are supposed to do, but they are supposed to turn the air conditioner on because the thermostat activates them, not your finger. Be very careful about sticking your finger in there.
Posted on Jul 22, 2008
SOURCE: circuit board fuse keeps poping
Traced wires and found the wires to the humidifer were the cuprits. I beleive the solenoid may be no good. After disconnecting the wires to the humidifier, A/C and Heat are working fine now .
Posted on May 29, 2009
I come across this one a lot. You need to switch the wires at power cord.
Posted on Oct 12, 2009
Remove ther thermostat wires at control board, put a jumper wire across R and G, if fan comes on after you install blower door cover and restore power, the problem is either the thermostat or the wiring.
If you dont have 24 v between r and c then either the
transformer is bad or there is a little 3amp car fuse in the circuit board that could be blown.
Posted on Jun 12, 2010
Tips for a great answer:
May 31, 2015 | Goodman Heating & Cooling
May 08, 2014 | Goodman Manufacturing Goodman GSC130421...
Aug 04, 2012 | Goodman GPC1342H21A Air Conditioner
Nov 07, 2010 | Heating & Cooling
Aug 31, 2009 | Goodman CLT24AER24 Air Conditioner
Jun 24, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 23, 2009 | Goodman CKL30AR30 Air Conditioner
Jan 14, 2013 | Goodman GPH1324H21A WallWindow Air...
Mar 20, 2012 | Goodman GPH1324H21A WallWindow Air...
85 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: