Question about Mitsubishi Mr. Slim MXZ30TN Air Conditioner
Compressor is likely shorted to ground. With a multimeter you could ohm the compressor to verify. With power off remove wires at compressor. Test each leg to ground or metal or a piece of copper. Continuity would confirm a grounded compressor. Warranty, age and cost would determine next step.
Posted on Jul 09, 2017
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Ok, it can be two things.
Posted on Apr 06, 2009
SOURCE: p8 eroor code
P8 error is abnormal pipe temperature indoor. If you are running it on heating P8 error will appear because the disc pressure is too high. It could be overcharged.
Posted on Jun 01, 2009
Have u checked at the compressor unit. There is a contactor than energizes the compressor is this contactor getting supply when u turn on the evaporator this contactor get energized see if this happens. If this is energized and you are getting supply to the compressor and compressor doesn't turn on 1.) compressor has thermal protection this might be faulty 2.) or the compressor has too much freon 3.) check if the windings of the compressor motor are not short to ground
Posted on Jul 24, 2009
SOURCE: a/c shut down /how to reseset
Reset the power with a 5 min gap on the outdoor isolator and indoor isolator (if applicable) then return with any fault codes/light flashing sequences which will be the fault coce, if it occurs again :)
Posted on Jul 05, 2010
Tips for a great answer:
Aug 07, 2015 | Sharp Heating & Cooling
Aug 16, 2014 | Electrical Supplies
Jul 15, 2012 | Haier Heating & Cooling
Jul 15, 2011 | Goldstar GW-HD5000 Window Air Conditioner
Sep 02, 2010 | Carrier 38CKC036 Air Conditioner
Jun 02, 2017 | Dometic Rooftop RV Air Conditioner
Jul 29, 2009 | Heating & Cooling
Apr 02, 2009 | Whirlpool ACQ158XP Wall/Window Air...
Sep 16, 2008 | Dometic Rooftop RV Air Conditioner
77 people viewed this question
Usually answered in minutes!