Question about Honeywell Heating & Cooling
I had that last night. I turned off the unit for a couple of hours and it came back on and ran and cooled. I have no friggin' idea if it will work but it got us through last night.
Posted on Jun 24, 2008
I have had the same problem- twice. It was a similar but different problem each time. The -AC means the ac control voltage isnt making it to the thermostat. In my case both times it was a switch in the control circuit that wasn't closing properly. The easiest was the front cover switch. If the front cover is removed from the furnace or has vibrated loose, the switch will open, preventing the furnace from running. The other instance I ran into was a flow switch on the exhaust blower which ensures the there is flow OUT the chimney. The switch wasn't functioning, so the furnace wouldn't start. The blower would come on for a short time, but the burners wouldn't light.
Hope this helps,
Posted on Dec 12, 2008
Tips for a great answer:
Sep 13, 2015 | Cars & Trucks
Jan 22, 2010 | Heating & Cooling
Nov 12, 2009 | Honeywell Power Humidifier: Furnace...
Nov 08, 2009 | Honeywell Programmable Thermostat Heater
Oct 14, 2009 | Honeywell Electronic Programmable...
Sep 27, 2009 | Honeywell Electronic Programmable...
Jan 06, 2009 | Honeywell Electronic Programmable...
Dec 30, 2008 | Honeywell Power Humidifier: Furnace...
May 24, 2017 | Honeywell Heating & Cooling
141 people viewed this question
Usually answered in minutes!