Question about Genie Company Health & Beauty
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Press and hold the homelink button and wait till the red light flashes slowly,but don't release it. Now hold a working remote 3 inches away,press the remote button and hold it.When the red Homelink buttom fllashes quickly, release both buttons. Now go to the opener and push the learn button. Now go back to your car and press and hold the Homelink button. You will see the lights on your opener flash. Now your Homelink button should operate your garage door.
Posted on Feb 09, 2009
If you have the wall control with 3 buttons one of them is the lock button. It is not on the side. If you have it and the light in the wall control is flashing, press and hold the button with the lock icon for 3 seconds and release. If that is not the situation your receiver is bad. The receiver is inside the motor unit and is part of the logic board.
Posted on Dec 30, 2009
Okay, I looked up the installation manual online to see exactly what you are working with.
Yes the R anc C need to be hooked to the transformer supplied with the unit. The primary 120v side needs to be hooked into the power coming into the furnace. this can easily be done were the L and N get hooked into your furnace or circuit board on the furnace. This will provide the contiuous power to the unit. Preferably you will hook this after the door switch of the furnace so that you will kill the power toit if you take the blower door off.
The ODT terminals are for the outdoor sensor if you want to hook that up it will vary the humidiy in your home according to the outdoor temperature then.
Now the W/G and Cf terminals. If you have 24v coming from the HUM terminals of your furnace you DO NOT need a second transformer. You must check your furnace manual or check the voltage to them with the furnace blower energized. The HUM terminals will only have power to them when the blower should be running.
If the HUM terminals are 120v then you need to get another transformer and hook up the primary side to the HUM terminals so it is powered only when the the blower is running. Hook the secondary side to the W/G and Cf terminals.
So bottom line is that you need to figure out what voltage your furnace is giving to the HUM terminals and then go from there. Some times the EAC terminals or the ACC terminals will be 24v on the furnace board. Either of them could be used also, as they are only energized when the blower is running also.
Posted on Jan 25, 2010
SOURCE: I have to replace the
All the terminals are connected together so it won't matter which terminal you use, just as long as you have the Herm, Com, and Fan wires correct. Hope this helps!
Posted on Sep 28, 2010
Tips for a great answer:
Nov 03, 2014 | Building Materials
Mar 22, 2014 | Genie garage door opener series ii wall...
May 03, 2017 | Transmitter Solutions Building Materials
Jul 07, 2011 | Sears Craftsman LiftMaster Chamberlain...
Dec 09, 2010 | Genie Company G912 Genie 912 One Button
Nov 23, 2010 | Sears Craftsman LiftMaster Chamberlain...
Aug 08, 2010 | liftmaster Chamberlain Garage Door Opener...
Sep 22, 2009 | Sears Craftsman LiftMaster Chamberlain...
Aug 18, 2009 | Genie Company IntelliCode GICT390-1BL...
105 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: