Question about Heating & Cooling
Recheck the wires to make sure that you are calling the outdoor unit to cool! Wires that call for cooling are R to Y and R to G calls indoor fan on! This usually happens at the same time in the thermostat when call for cooling is tripped, Green wire turn signal to indoor fan on and Yellow wire fire 24v to the contactor oudoors to the compressor and outdoor fan. Check all wires for contact an breaks.
Posted on Aug 22, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 13, 2011 | Honeywell Programmable Thermostat Heater
Dec 14, 2010 | Honeywell Electronic Programmable...
Dec 02, 2010 | Honeywell Programmable Thermostat Heater
Apr 29, 2017 | Honeywell Programmable Thermostat Heater
Oct 31, 2010 | Honeywell Focus 6300B 5-2 Days...
Feb 07, 2010 | Honeywell Electronic Programmable...
Nov 14, 2009 | Honeywell Programmable Thermostat Heater
Jan 25, 2009 | Honeywell Electronic Programmable...
122 people viewed this question
Usually answered in minutes!