Question about Heating & Cooling
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
You almost have it Look closer at the run capacitor. It has Herm, this is for the compressor, Com or C and F or Fan.
1 of your power wires is the fan speed so connect them accordingly usually black is hi, blue med, & red is low. You are "feeding" voltage to the selector switch on 1 side and coming out to the fan motor speeds.
Next you have a "Common" wire on your fan motor (this means its Common to all the other connections inside the fan motor to me. It is usually white. Connect this to the other line of power usually the Com on the capacitor unless it connects to a strip on the selector switch. But 1 of these 2 places will be the other side of your Power when plugged in. Lastly the brown it is usually the fan capicator only wire and it will connect to the fan "F" terminal on the capicator this terminal will not have any other wires connected to it.
This should make you a happy camper. Please rate me accordingly and good luck.
Posted on Mar 08, 2009
SOURCE: I am replacing the a/c
Brown wire is Start
Yellow wire is run or Power
Black wire is High Speed or Common
The other two taps are speed taps, but you have a single speed application
And high speed is what you need ,that’s why there’s not any wires
on Red and Blue if high speed was to much then you would move the
Black wire to one of the other taps RED low speed or Blue Medinm speed
White goes to the Yellow wire from the capacitor
Black goes to the Black wire you took off of high speed on old motor
Of course both Brown wires go to the capacitor and Green to ground
If a capacitor doesn’t discharge it doesn’t mean it’s bad
but the capacitors don’t last as long as they used.
Any time you put in a new motor always replace the capacitor
It will save you a lot of time and grief later on.
Posted on Apr 28, 2009
There should be a wiring diagram on the back of the access panel. If you can't read it, check online for model wiring diagram. Don't guess, you may cause more expensive damage.
Posted on Jun 26, 2009
Before attempting any of these recommendations, First disconnect all the power sources and check your wiring diagrams on the motor and condensing unit.
On the old capacitor if you look on the top near each of the three terminals. Are they marked, fan - C - herm? If they are that is a dual capacitor and that needs to stay because that is also your compressor capacitor.
The Red wire from the conductor is Run and it's connected to C on the old capacitor.
Follow the Yellow wire and see if it goes to the S or start terminal on the compressor, if it does then that is the Start wire for your compressor and it connects to herm on the capacitor.
For the fan motor a lot of times the wiring connections are printed on the motor label.
Check the label, Purple should be run and connect to C on the old capacitor.
Black should be Common and it connects to the opposite side of the contactor as the Red wire. If the Red wire connects to T1 then the Black wire connects to T2.
The Brown wire shoud be the start wire on the fan motor and it connects to the Fan terminal on the old capacitor.
Now if you want to use the new fan capacitor. Take the Purple wire from the motor and look for any marks (red paint or a dash) on or beside the terminals on the new capacitor. If there is an identifying mark then connect the Purple wire to that terminal, if no marks you can connect it to either terminal. Then you need a jumper wire from C on the old capacitor to the purple side of the new capacitor. Then take the brown wire and connect it to opposite terminal of the new capacitor.
Posted on Apr 06, 2010
Tips for a great answer:
Jan 31, 2014 | Hunter 21617 Palermo Brushed Nickel...
Jun 03, 2011 | Hunter 52" Ceiling Fan With Light And...
Oct 25, 2010 | Hunter Ceiling Fans Individual...
Jun 09, 2010 | Hunter 20485 The Wellesley Taupe Ceiling...
May 01, 2010 | Hunter (25417) Ceiling Fan
May 24, 2009 | Hunter 23827 Classic Original White 42"...
Aug 03, 2008 | Dryers
Apr 13, 2008 | Hunter Dryers
127 people viewed this question
Usually answered in minutes!