Question about Fujitsu 24C1 Air Conditioner
Sounds like the drain needs cleaning if not clean the unit complete
inside pan and coils with a coil cleaner purchased at your Appliance repair store or A/C parts and Repair shop.
Don't forget to tilt the unit back a bit off level.
If this was helpful please rate me.
Leo Ponder Appliance-Tyler,Texas
Posted on Aug 21, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
This can be due to three reasons. The water drain pipe is block. Which can be sucked clean with wet/dry vacuum cleaner. The drain pipe behind the unit is not sloping downward away from the unit. Or the coils of the internal could be iced up. If this is the case the unit should be switched of until the ice is completely melted and switch the unit on again. If the copper pipes leaving the the condenser unit outside is starting to freeze up, the unit is short of gas. Call a A/C company to refill the gas and search for possible gas leaks.
Posted on Jan 26, 2010
Typically if you go outside directly behind the inside unit you will probably see a white colored tube, this is the drain and if you have a wet/dry vacuum you can clear it with that. The actual drain can vary but it makes sense to exit and drain asap.
Posted on Jun 19, 2011
Tips for a great answer:
Feb 23, 2015 | Fujitsu Heating & Cooling
Jul 11, 2011 | Fujitsu 24R1 Air Conditioner
Jan 28, 2011 | Fujitsu 24C1 Air Conditioner
Jan 16, 2011 | Fujitsu Heating & Cooling
Dec 26, 2010 | Fujitsu Heating & Cooling
Nov 08, 2009 | Fujitsu 24C1 Air Conditioner
Jun 16, 2009 | Heating & Cooling
Jun 03, 2007 | Fujitsu 24C1 Air Conditioner
541 people viewed this question
Usually answered in minutes!